Phase Technologies Motor Protection filters are designed with distributed gap alloy powder
cores resulting in superior peak voltage reduction, lower core losses, higher temperature
stability, and a more compact product envelope.
Remotely monitor and control
your VFD's and other devices.
1LH, 3LH, and DX - Signature and Performance Chassis
QUICKSTART LH-DX, Revision 002
1LH/3LH/DX, Performance and Signature Chassis
Mounting the VFD
Mount the enclosure in such a way that it is fully supported. Note: 18" (450mm) clearance below and 6" (150mm) around required for ventilation.
Open door after turning door latches 1/4 turn counter-clockwise.
Connect motor leads to the terminal block labeled output.
Optional: If your VFD is equipped with AuxPower®, make the connection to your pivot on the output terminals located in the upper right-hand area of the chassis.
Connect power leads to the terminals labeled input. Note: This may be on the optional disconnect.
Caution: Crimp or solder (NO WIRE NUTS) any connections when splicing motor leads.
can cause nuisance faults or damage to the pump and VFD.
Input, output, and ground terminals
Secure the appropriate ground wires into the lugs marked with the ground symbol. Note: 4ohms or less to earth ground recommended
Install transducer into a 1/4" NPT non-metallic
fitting and run the wire back to the VFD, up to the terminal area and cut to length. Note: Cut transducer leads to length, DO NOT coil extra wire or connect shielding ground wire.
DO NOT run transducer leads next to motor leads. If necessary, only cross transducer and motor leads at a 90 degree angle.
Install the Black wire into the I1- terminal and the remaining White or Red wire into the I1+ terminal on the control board.
Terminal blocks used for connecting analog transducer
Powering up the VFD
Close the door and secure by turning door latches 1/4 turn clockwise.
To bypass initial setup, press the HOME button, or, to
use the Perfect Pressure wizard, choose Yes (ENTER) when prompted.
Note: Hold the BACK and ENTER buttons for 3 seconds to reset the VFD to default configuration
Optional: To add a run/stop from a PLC, pivot control, or float switch remove the orange jumper wire and make those connections to
AUX2 and COM. Caution: No voltage may be introduced on these terminals.