Phase Technologies Motor Protection filters are designed with distributed gap alloy powder
cores resulting in superior peak voltage reduction, lower core losses, higher temperature
stability, and a more compact product envelope.
Remotely monitor and control
your VFD's and other devices.
Mount the enclosure using provided brackets in such a way that it is fully supported. Note: 6" (150mm) clearance above/below and 3" (75mm) around required for ventilation.
Remove screws necessary to remove cover.
Connect motor leads to the terminal block labeled output.
Connect power leads to the terminals labeled input.
Caution: Crimp or solder (NO WIRE NUTS) any connections when splicing motor leads.
can cause nuisance faults or damage to the motor and VFD.
DXL 450 Input and Output Terminals
Secure the appropriate ground wires into the lugs marked with the ground symbol. Note: 4ohms or less to earth ground recommended
DXL 4350 Input Lugs above Output Lugs
Note: For single-phase input, connect incoming power to L1 and L2. See derate chart in manual for current ratings.
If using transducer, install into a 1/4" NPT non-metallic
fitting and run the wire back to the VFD, up to the terminal area and cut to length. Note: Cut transducer leads to length, DO NOT coil extra wire or connect shielding ground wire.
DO NOT run transducer leads next to motor leads. If necessary, only cross transducer and motor leads at a 90 degree angle.
Install the Black wire into the I1- terminal and the remaining White or Red wire into the I1+ terminal on the control board.
Terminal blocks used for connecting external inputs/outputs
Powering up the VFD
Replace the cover and reinstall previously removed screws.
To bypass initial setup, press the HOME button, or, to
use the Perfect Pressure wizard, choose Yes (ENTER) when prompted.
Note: Hold the BACK and ENTER buttons for 3 seconds to reset the VFD to default configuration
Optional: To add a run/stop from a PLC, float switch, or similar, remove the orange jumper wire and make those connections to
AUX2 and COM. Caution: No voltage may be introduced on these terminals.